With the size of turbines increasing, the wind industry needs to learn about the importance of fire safety in wind turbines. Fire is the second leading cause of accidents in wind turbines after blade failure. As our reliance grows on wind turbines, keeping them fully operational and at reduced levels of risk becoming more important, and as a result, so does safety management. 10-30% of all loss-of-power-generation incidents in wind power plants are due to fire. Fires in wind turbines not only lead to a loss of business continuity and a negative impact on the company’s reputation but also, most importantly, are a critical safety issue.
With predictions of much taller and more powerful turbines and thus fewer per project, ensuring that the they are in working order is essential, because the larger and fewer the turbines, the more costly they will be to operators in the event of fire damage. Due to the height and location of wind turbines, classic firefighting methods come up against their limits and therefore fire extinguishing systems that use gases such as carbon dioxide, inert gases or clean agents such as FM 200 fire suppression system® and Novec™1230, which are especially appropriate for dealing with fires in electrical systems because they extinguish the fire quickly whilst not damaging the electrical systems or the compartment in which they are being discharged.
However, it is important to note that such fire extinguishing systems require maintenance to ensure they are fully operational and ready in event of a fire. ISO 14520-1:2015(E) assumes that these systems accidentally discharge and leak. 184.108.40.206 Contents indication: “Means shall be provided to indicate that each container is correctly charged.” Followed by “220.127.116.11 The storage container contents shall be checked at least every six months as follows. a) Liquefied gases: for halocarbon agents, if a container shows a loss of agent in quantity of more than 5 % or a loss of pressure (adjusted for temperature) of more than 10 %, it shall be refilled or replaced.”